ASME SA213, ASTM A213 / A 213M T11, T12, T22, T2, T5, T5b, T5c, T9, T91 is the standard applicable to seamless alloy-Steel Boiler, Superheater, and Heat-Exchanger Tubes.
ASME SA213 /SA213M tubes shall be made by the seamless process and shall be either hot-finished or cold finished as specified.
ASME SA213 /SA213M covers several grades of minimum- wall-thickness, seamless, alloy-steel, boiler and superheater tubes.
ASME SA213 /SA213M tubing sizes and thicknesses usually furnished to this specification are 1⁄8 in. [3.2 mm] in inside diameter to 5 in. [127 mm] in outside diameter and 0.015 to 0.500 in. [0.4 to 12.7 mm], inclusive, in minimum wall thickness or, if specified in the order, average wall thickness. Tubing having other diameters may be furnished, provided such tubes comply with all other requirements of this specification.
Standard: ASME SA213 /SA213M
Description Name: ASME SA213 / ASTM A213 T11 Seamless tubes, ASTM A213 / ASME SA213 T12 Seamless tubes, ASTM A213 / ASME SA213 T22, Seamless alloy tubes, ASTM A213 T11 Superheater tubes, ASTM A213 T12 Superheater tubes, ASTM A213 T22 Superheater tubes, ASTM A213 T11 boiler tubes, ASTM A213 T22 boiler tubes, ASTM A213 T12 boiler tubes, Seamless superheater tubes, Boiler tubes.
Size: 3.2 to 127 mm
Wall Thickness: 0.4 to 12.7mm
Length: Single random length/ Double random length or as customer’s actual request
Grade: T11, T12, T22
ASTM A 1016/A 1016M Specification for General Requirements for Ferritic Alloy Steel, Austenitic Alloy Steel, and Stain- less Steel Tubes.
Chemical Components (%)
Heat Treatment Requirements
|Grade||UNS Number||Heat Treat Type||Subcritical Annealing or Tempering Temperature, Min or range °F [°C]|
|T11||K11597||full or isothermal anneal normalize and temper||1200 |
|T12||K11562||full or isothermal anneal normalize and temper subcritical anneal||1200 to 1350[650 to 730]|
|T22||K21590||full or isothermal anneal normalize and temper||1250 |
Tensile Requirements and Hardness
|Strength (Mpa)||Strength (Mpa)||(%)||(HRB)|
- Flattening Test—One flattening test shall be made on specimens from each end of one finished tube, not the one used for the flaring test, from each lot
- Flaring Test—One flaring test shall be made on specimens from each end of one finished tube, not the one used for the flattening test, from each lot
- Hydrostatic or Nondestructive Electric Test—Each tube shall be subjected to the nondestructive electric test or the hydrostatic test. The type of test to be used shall be at the option of the manufacturer, unless otherwise specified in the purchase order.
Materials and Manufacture
Get in Touch
If you are interested in our products or service, please contact us now.
Tel.: +86 185 5109 0083 | E-mail: firstname.lastname@example.org